# Power Flow¶

See the module `pypsa.pf`

.

## Full non-linear power flow¶

The non-linear power flow `network.pf()`

works for AC networks and
by extension for DC networks too (with a work-around described below).

The non-linear power flow `network.pf()`

can be called for a
particular `snapshot`

as `network.pf(snapshot)`

or on an iterable
of `snapshots`

as `network.pf(snapshots)`

to calculate the
non-linear power flow on a selection of snapshots at once (which is
more performant than calling `network.pf`

on each snapshot
separately). If no argument is passed, it will be called on all
`network.snapshots`

.

### Non-linear power flow for AC networks¶

The power flow ensures for given inputs (load and power plant dispatch) that the following equation is satisfied for each bus :

where is the complex voltage, whose rotating angle is taken relative to the slack bus.

is the bus admittance matrix, based on the branch impedances and any shunt admittances attached to the buses.

For the slack bus it is assumed is given and that ; P and Q are to be found.

For the PV buses, P and are given; Q and are to be found.

For the PQ buses, P and Q are given; and are to be found.

If PV and PQ are the sets of buses, then there are real equations to solve:

To be found: and .

These equations are solved using the Newton-Raphson method, with the Jacobian:

and the initial “flat” guess of and for unknown quantities.

### Line model¶

Lines are modelled with the standard equivalent PI model. In the future a model with distributed parameters may be added.

If the series impedance is given by

and the shunt admittance is given by

then the currents and voltages at buses 0 and 1 for a line:

are related by

### Transformer model¶

The transformer models here are largely based on the implementation in pandapower, which is loosely based on DIgSILENT PowerFactory.

Transformers are modelled either with the equivalent T model (the
default, since this represents the physics better) or with the
equivalent PI model. The can be controlled by setting transformer
attribute `model`

to either `t`

or `pi`

.

The tap changer can either be modelled on the primary, high voltage
side 0 (the default) or on the secondary, low voltage side 1. This is set with attribute `tap_side`

.

If the transformer `type`

is not given, then `tap_ratio`

is
defined by the user, defaulting to `1.`

. If the `type`

is given,
then the user can specify the `tap_position`

which results in a
`tap ratio`

given by:

For a transformer with tap ratio on the primary side
`tap_side = 0`

and phase shift , the
equivalent T model is given by:

For a transformer with tap ratio on the secondary side
`tap_side = 1`

and phase shift , the
equivalent T model is given by:

For the admittance matrix, the T model is transformed into a PI model with the wye-delta transformation.

For a transformer with tap ratio on the primary side
`tap_side = 0`

and phase shift , the
equivalent PI model is given by:

for which the currents and voltages are related by:

For a transformer with tap ratio on the secondary side
`tap_side = 1`

and phase shift , the
equivalent PI model is given by:

for which the currents and voltages are related by:

### Non-linear power flow for DC networks¶

For meshed DC networks the equations are a special case of those for AC networks, with the difference that all quantities are real.

To solve the non-linear equations for a DC network, ensure that the
series reactance and shunt susceptance are zero
for all branches, pick a Slack bus (where ) and set all
other buses to be ‘PQ’ buses. Then execute `network.pf()`

.

The voltage magnitudes then satisfy at each bus :

where all quantities are real.

is based only on the branch resistances and any shunt conductances attached to the buses.

### Inputs¶

For the non-linear power flow, the following data for each component are used. For almost all values, defaults are assumed if not explicitly set. For the defaults and units, see Components.

bus.{v_nom, v_mag_pu_set (if PV generators are attached)}

load.{p_set, q_set}

generator.{control, p_set, q_set (for control PQ)}

storage_unit.{control, p_set, q_set (for control PQ)}

store.{p_set, q_set}

shunt_impedance.{b, g}

line.{x, r, b, g}

transformer.{x, r, b, g}

link.{p_set}

Note that the control strategy for active and reactive power PQ/PV/Slack is set on the generators NOT on the buses. Buses then inherit the control strategy from the generators attached at the bus (defaulting to PQ if there is no generator attached). Any PV generator will make the whole bus a PV bus. For PV buses, the voltage magnitude set point is set on the bus, not the generator, with bus.v_mag_pu_set since it is a bus property.

Note that for lines and transformers you MUST make sure that is non-zero, otherwise the bus admittance matrix will be singular.

### Outputs¶

bus.{v_mag_pu, v_ang, p, q}

load.{p, q}

generator.{p, q}

storage_unit.{p, q}

store.{p, q}

shunt_impedance.{p, q}

line.{p0, q0, p1, q1}

transformer.{p0, q0, p1, q1}

link.{p0, p1}

## Linear power flow¶

The linear power flow `network.lpf()`

can be called for a
particular `snapshot`

as `network.lpf(snapshot)`

or on an iterable
of `snapshots`

as `network.lpf(snapshots)`

to calculate the
non-linear power flow on a selection of snapshots at once (which is
more performant than calling `network.lpf`

on each snapshot
separately). If no argument is passed, it will be called on all
`network.snapshots`

.

For AC networks, it is assumed for the linear power flow that reactive power decouples, there are no voltage magnitude variations, voltage angles differences across branches are small and branch resistances are much smaller than branch reactances (i.e. it is good for overhead transmission lines).

For AC networks, the linear load flow is calculated using small voltage angle differences and the series reactances alone.

It is assumed that the active powers are given for all buses except the slack bus and the task is to find the voltage angles at all buses except the slack bus, where it is assumed .

To find the voltage angles, the following linear set of equations are solved

where is the incidence matrix of the network, is the diagonal matrix of inverse branch series reactances multiplied by the tap ratio , i.e. and is the phase shift for a transformer. The matrix is singular with a single zero eigenvalue for a connected network, therefore the row and column corresponding to the slack bus is deleted before inverting.

The flows `p0`

in the network branches at `bus0`

can then be found by multiplying by the transpose incidence matrix and inverse series reactances:

For DC networks, it is assumed for the linear power flow that voltage magnitude differences across branches are all small.

For DC networks, the linear load flow is calculated using small voltage magnitude differences and series resistances alone.

The linear load flow for DC networks follows the same calculation as for AC networks, but replacing the voltage angles by the difference in voltage magnitude and the series reactance by the series resistance .

### Inputs¶

For the linear power flow, the following data for each component are used. For almost all values, defaults are assumed if not explicitly set. For the defaults and units, see Components.

bus.{v_nom}

load.{p_set}

generator.{p_set}

storage_unit.{p_set}

store.{p_set}

shunt_impedance.{g}

line.{x}

transformer.{x}

link.{p_set}

Note that for lines and transformers you MUST make sure that is non-zero, otherwise the bus admittance matrix will be singular.

### Outputs¶

bus.{v_mag_pu, v_ang, p}

load.{p}

generator.{p}

storage_unit.{p}

store.{p}

shunt_impedance.{p}

line.{p0, p1}

transformer.{p0, p1}

link.{p0, p1}